HOME > Legionella: what site managers can learn from the Bibby Stockholm case
On Friday 11th August 2023, 39 asylum seekers who were being housed on the ‘Bibby Stockholm’ barge in Dorset were temporarily removed following the discovery of Legionella in the barge’s water systems.
Our Technical Director, Bob Harris, was invited by BBC News to provide an expert overview of the management factors that could have played a role in this high-profile case. You can watch the coverage below.
Legionella risk is a fact of life on ships and barges, but site managers with a duty to manage water systems in buildings onshore can also take important lessons from this case, since the water systems in buildings can be remarkably similar to those on a barge.
We’ve summarised four of these lessons below.
As we know, Legionella is a naturally occurring water-borne pathogen.
It’s present in the rivers that feed our reservoirs, and even if we treat that water before it reaches the water supply that businesses and homes use, extremely small numbers of the bacteria may still enter our buildings’ water systems.
In extremely small quantities, Legionella bacteria presents a low risk to human health. However, once it enters your water system, and if the conditions are right (including stagnant water, temperature between 20-45°C and a food source such as rust, organic material or biofilm) it can rapidly multiply to dangerous concentrations.
In the case of the Bibby Stockholm, we still don’t have all the information but, the timeline of the emergence of Legionella was as follows:
In short: don’t give Legionella bacteria the opportunity to thrive in your water system. The best way to do this is by following Lesson 2.
If you are responsible for looking after your site’s water systems, starting with commissioning a Legionella risk assessment will be a key requirement of your duties. It is very important that the risk assessment is done before anything else.
The risk assessment gives you a full view of your water system, the risks inherent in it, and the exact control measures you will need to take to minimise those risks. If you already have a Legionella risk assessment, it is important to review this regularly. You must also review it if you make any changes to your water system or if the use of your buildings or site changes.
If you delay your risk assessment and only react to problems as they arise, you won’t have a clear picture of the work that is needed to put in place any remedial work or regular monitoring to support your water system and ensure that regular Legionella compliance checks are taking place.
Bear in mind, you are at risk of breaching the law if you fail to implement control measures based on a completed risk assessment.
The main purpose of water sampling is to confirm that your water systems are safe. Although routine water sampling for the presence of Legionella is not normally required in most hot and cold water systems, it may be required in certain circumstances, such as where your risk control measures fail or if an outbreak of Legionnaires’ disease is suspected.
It’s a legal requirement in some systems, such as industrial cooling systems or potable water tanks as well as in hospitals (to protect immunocompromised people who are more likely to contract Legionella).
However, even if you aren’t required by law to take samples, it’s a valuable tool for reassurance if you think your water system could be vulnerable, regardless of its complexity.
A barge’s water system is comparable to a complex water system like you might find in a hotel (with leisure pools, showers, tanks, and hot water cylinders).
Larger, more complex water systems can prove difficult to fully understand in terms of Legionella risk, and if your risk assessment is based on a poor understanding of its operation, you may inadvertently put ineffective controls in place.
The Legionella risk assessment is the foundation of your Legionella management system. If it is flawed, its recommendations may be inaccurate and the controls ineffective, leaving occupants at risk and your organisation out of compliance.
Simply put, there’s no place for doubt. Expert support to interpret your water systems will help you conduct a comprehensive risk assessment, which means that every recommended control measure will minimise the risk presented by Legionella bacteria – and keep you compliant.
While no two water systems are the same, following the advice above and implementing many of the same basic measures (such as temperature control and regular inspections and cleaning) will help secure your building’s system against Legionella.
If you have any doubts about the order in which you should carry out your duties, there are three basic stages to risk mitigation that you should always follow:
1) Use a risk assessment to understand your water system and the risk of Legionella in your system.
2) Implement the recommended measures to control those risks, and carry out any remedial works to bring your water systems into compliance.
3) Make sure Legionella bacteria doesn’t get an opportunity to grow in your water system with an ongoing monitoring, inspection and testing programme.
Are you responsible for managing Legionella risk in your building’s water system? You can use our Risk Assessment flowchart to see what steps you may need to take to secure it.
However, if you have any questions about the steps above, your Legionella management strategy or the condition of your water system, don’t hesitate to ask our expert team for advice here, or by calling 0203 384 6175.